General topics about all things heating, ventilation, air conditioning and refrigeration.
2 posts • Page 1 of 1
I have a gmp100-3 goodman gas furnace. When it calls for heat the main blower comes on and the status light blinks four times. according to the code, it's telling me the high limit or the auxillary limit is open, i replaced the high limit but it's still doing the same thing. Could both limit switches be bad?