Thanks for the quick response, and sorry for the delay in responding.
Ended up in calling an HVAC tech. for a service call. Deemed it not a pressure switch nor flame sensor. He looked over things and measured the intake temp and output temp was reading well over 70 degrees difference. The fan was already blowing on the high setting with good volume, so he measured the gas pressure which was reading a 4 and reduced it to 2 1/2. That did drop the temp to a 58 degree difference which is what the furnace is rated for. It ran the rest of the day normally.
The next day it started to short cycle again, made the call. He came out and checked over things decided to run a new ground to the furnace stating hes seen this problem in the past as well. Furnace ran fine, stated the next thing would be a control board and a pressure switch ( because the pressure switch is an inexpensive part ).
Well needless to say it started short cycling again, decided to start throwing parts at it my self at this point. Have replaced the pressure switch (no change), now have replaced the control board and again no change.
So new ground wire, new pressure switch, new control board. Flame sensor is relatively new and has been cleaned.
Furnace will fir up when cold and run for a good 10 minutes and then start short cycling (10 to 15 sec intervals).
All vents are open, filter clean and have even run without the filter (no change)
Any thoughts, suggestions, recommendations greatly appreciated.