Problems related to residential installations.
5 posts • Page 1 of 1
Hope someone can help me with this problem. I have a 9 year old Luxaire furnace that is not firing. I removed the cover and the flashing light indicates that there is a problem with the pressure switch. The fan is running but the is no flame or ignition, I have tried turning everything off and back on again after a few minutes. Any advise would be great!
Anything resticting your vent, a opened cover of a sealed combustion chamber, failing vent motor or capaciter, vent blower loose on shaft, split ends or holes on pressure tubes, water in the pressure tubes, loose wire connections to PS or safety circuit, faulty diaphram or electical switch in PS, cracked heat exchanger, faulting motherboard but the most common cause is a debris build up where the pressure tube connects to the blower assy. Remove the tube from the vent blower and stick a straightened paper clip into the vent blower hole to see if it's plugging up. Check the pressure switch opening at the same time for debris.