General topics about all things heating, ventilation, air conditioning and refrigeration.
My condenser fan is making noise and eventually slows down and stops running if it has to run for an extended period of time. I have ordered a motor (part 51-21853-01) from NorthAmericanHVAC but it won't be here until Friday. My question is the motor says it requires a 3uf 370 volt capacitor. The one that is currently in there is a 40+3uf 440 volts. Will this work or do I have to replace it?
Thanks - Jerry
- New Contributor
- Posts: 9
- Joined: Thu Jan 27, 2011 3:14 pm
Always replace/use the capacitor with an identical one or use the one that the manufacturer calls for. Using the wrong capacitor can burn our a motor very quickly. 330 or 440 volts doesn't matter but the microfarad value(s) are critical.
- Most Valued Contributor
- Posts: 998
- Joined: Sat Jun 18, 2011 11:26 am
Return to HVAC General Forum